The Lindi Corp| Licence #008208 & #0077981 | 50 N. Sandhill Blvd. Mesquite, NV 89027 | 702-346-5850 | email@example.com | www.thelindicorp.com
|Air Conditioning Repair
One of the most common air conditioning problems is improper operation. If your air conditioner is on, be sure to close
your home's windows and outside doors. For room air conditioners, isolate the room or a group of connected rooms as
much as possible from the rest of your home.
Other common problems with existing air conditioners result from faulty installation, poor service procedures, and
inadequate maintenance. Improper installation of a central air conditioner can result in leaky ducts and low airflow. Many
times, the refrigerant charge (the amount of refrigerant in the system) does not match the manufacturer's specifications.
If proper refrigerant charging is not performed during installation, the performance and efficiency of the unit is impaired.
Unqualified service technicians often fail to find refrigerant charging problems or even worsen existing problems by
adding refrigerant to a system that is already full. Learn what to ask for when hiring a technician to maintain your air
Air conditioner manufacturers generally make rugged, high quality products. If your air conditioner fails, begin by
checking any fuses or circuit breakers. Let the unit cool down for about five minutes before resetting any breakers. If a
central air conditioner's compressor stops on a hot day, the high-pressure limit switch may have tripped; reset it by
pushing the button, located in the compressor's access panel.
refrigerant is not a solution. A trained technician should fix any leak, test the repair, and then charge the system with the
correct amount of refrigerant. Remember that the performance and efficiency of your air conditioner is greatest when the
refrigerant charge exactly matches the manufacturer's specification, and is neither undercharged nor overcharged.
Refrigerant leaks can also be harmful to the environment.
of air coming into the evaporative coil. If the sensor is knocked out of position, the air conditioner could cycle constantly
or behave erratically. The sensor should be near the coil but not touching it; adjust its position by carefully bending the
wire that holds it in place.
common when a system is oversized. Because corrosion of wire and terminals is also a problem in many systems,
electrical connections and contacts should be checked during a professional service call.
conditioners may not drain properly if not mounted level.
compressor or fans are likely to fail prematurely.